This new and improved Warrior model boasts increased power and a fully compliant EU5 standard engine, with a brushed copper alternator within that produces a steady motor speed.
It features a Automatic Voltage Regulator (AVR) control system to monitor the output and protect the unit against voltage fluctuations, providing a smoother sine wave.
Enclosed by a soundproof canopy, coated with a chip resistant matt finish, the durable heavy-duty industrial frame provides full protection and aids portability. This silent enclosure has the added benefit of a key start facility and smooth running is further enhanced by the addition of anti-vibration mountings.
A fully fuelled 16 litre tank could easily achieve up to 12 hours running at around 50% load, making this Warrior generator ideal for all sorts of applications such as domestic supply, construction, catering and industrial use with for example power tools & lighting units. As a standby generator it is the perfect product during power cuts and outages, and is even supplied with an Automatic Transfer Switch (ATS) Input Port compatible with our ATS Panel to automatically start up the Generator when loss of power is detected & stop it when the mains supply is restored.
Fitted with 12v battery charging outlet and with 240v and 110v single phase output sockets as well as ATS Input Port for ATS panel 190102000010.
Please Note: Dual voltage generators will only give approx. 50-60% of the rated output on the lower voltage.
|AC Load||1 x 120V 32amp / 1 x 240V 32amp|
|Fuel Capacity||16 Litres|
|Oil Capacity||1.1 Litres|
|Low Oil Shutoff||Automatic|
|Noise Level @ 7m||68 dBA|
|88 x 59 x 73 cm|
|Weight||168 kg (370 lbs)|
|Operation at 50%||>12 hours|
|Certification||CE,EU Stage V,ISO9001-2000,GS,TUV|
|Warranty||2 Year Limited Warranty|
Most motor-driven products that you will connect to your generator need extra watts when they start, this is known as starting watts.
The Starting Watts listed on your generator is the wattage the generator can output for an average of 6 seconds (Inverter) or 10 minutes (Open Frame Type).
Once this period is over, and if the wattage has not reduced the Overload Protection will activate and the generator will trip using the following methods circuit breaker (frame type) and flashing overload light (Inverter), if this happens the power (wattage) needs to reduced or disconnected immediately and the generator needs to be reset by stopping the generator and turning everything to the ‘OFF’ position and leaving for minimum 2 minutes (Inverter Only).
The Maximum Watts listed on your generator is the MAX watts output the generator can run at – however it is not recommended to run your generator at the maximum watts for periods more than average 5 minutes (Inverter) and 60 minutes (Open Frame Type). Once this period is over, and if the wattage has not reduced the Overload Protection will activate and the generator will trip using the following methods circuit breaker (frame type) and flashing overload light (Inverter), if this happens the power (wattage) needs to reduced or disconnected immediately and the generator needs to be reset by stopping the generator and turning everything to the ‘OFF’ position and leaving for minimum 2 minutes. While working in the max zone on an Inverter you will have solid red overload light this is normal.